Displacement ventilation (DV) It is a room air distribution strategy where conditioned outdoor air is supplied at a low velocity from air supply diffusers located near floor level and extracted above the occupied zone, usually at ceiling height.
A typical displacement ventilation system, such as one in an office space, supplies conditioned cold air from an air handling unit (AHU) through a low induction air diffuser. Diffuser types vary by applications. Diffusers can be located against a wall ("wall-mounted"), at the corner of a room ("corner-mounted"), or above the floor but not against a wall ("free-standing"). The cool air accelerates because of the buoyancy force, spreads in a thin layer over the floor, reaching a relatively high velocity before rising due to heat exchange with heat sources (e.g., occupants, computers, lights). Absorbing the heat from heat sources, the cold air becomes warmer and less dense. The density difference between cold air and warm air creates upward convective flows known as thermal plumes. Instead of working as a stand-alone system in interior space, displacement ventilation system can also be coupled with other cooling and heating sources, such as radiant chilled ceilings or baseboard heating.
Displacement ventilation was first applied in an industrial building in Scandinavia in 1978, and has frequently been used in similar applications, as well as office spaces, throughout Scandinavia since that time. By 1989, it was estimated that Displacement ventilation comprised the 50% in industrial applications and 25% in offices within Nordic countries. Applications in the United States have not been as widespread as in Scandinavia. Some research has been done to assess the practicality of this application in U.S. markets due to different typical space designs and application in hot and humid climates, as well as research to assess the potential indoor environmental quality and energy-saving benefits of this strategy in the U.S. and elsewhere.
Displacement ventilation has been applied in many famous building such as the Suvarnabhumi International Airport in Bangkok, Thailand, the NASA Jet Propulsion Laboratory Flight Projects Center building, and the San Francisco International Airport Terminal 2 among other applications.
The thermal plumes and supply air from diffusers, which determines the velocity of airflow at floor level, play an important role in DV systems. It is necessary to carefully set the airflow rate from the diffuser to avoid drafts.
Due to the unique properties of thermal stratification, Displacement ventilation is typically used for cooling rather than for heating. In many cases, a separate heating source, such as a radiator or baseboard, is used during heating periods.
Displacement ventilation is best suited for taller spaces (higher than 3 meters [10 feet]). Standard mixing ventilation may be better suited for smaller spaces where air quality is not as great a concern, such as single-occupant offices, and where the room height is not tall (e.g., lower than 2.3 meters [7.5 feet]).
Benefits and Limitations
Local discomfort: vertical temperature difference and draft
Displacement ventilation systems are quieter than conventional overhead systems with better ventilation efficiency. Hence, it could enhance indoor air quality and provide desirable acoustic environment. Displacement ventilation systems are appropriate in space where high ventilation is required, such as classrooms, conference rooms, and offices.
Displacement ventilation can be a cause of discomfort due to the large vertical temperature gradient and drafts. According to Melikov and Pitchurov's research, sensations of cold caused by vertical temperature difference and draft are usually occurred at the lower leg/ ankle/ feet region, while warm sensations at the head are reported. The research also indicates, that the draft rating model could predict the draft risk with good accuracy in rooms with displacement ventilation systems.
There is a tradeoff inherent in these two issues: by increasing the flow rate (and the ability to remove greater thermal loads), the vertical temperature gradient can be reduced, but this could increase the risk of drafts. Pairing displacement ventilation with radiant chilled ceilings is an effort to mitigate this problem. According to some studies, displacement ventilation systems can only provide acceptable comfort if the corresponding cooling load is less than about 13 Btu/h-sf or 40 W/m2.
Indoor air quality
One benefit of displacement ventilation is possibly the superior indoor air quality achieved with exhausting contaminated air out of the room. Better air qualty is achieved when the pollution source is also a heat source.
The effectiveness of displacement ventilation at removing particulate contaminants has been investigated recently. Small aqueous droplets containing infectious nuclei are frequently released in hospital rooms and other indoor spaces, and tend to settle through the ambient air at a speed of order 1–10 mm/s typically. In cold climates or seasons, sufficiently small droplets are extracted from the top of a displacement-ventilated space if the mean upward air speed exceeds the particle settling speed. However, laboratory experiments have shown that larger droplets may settle faster than the air moves. In this case, the large droplets are not extracted effectively from a space with upward displacement ventilation, and their concentration increases if the ventilation rate is increased. In warmer climates or seasons, large-scale instabilities in the concentration of contaminants may occur within a space with downward displacement ventilation.
Some studies have demonstrated that displacement ventilation may save energy as compared to standard mixing ventilation, depending on the use type of the building, design/massing/orientation, and other factors. However, for the evaluation of energy consumption of displacement ventilation, the numerical simulation is the main method, since yearly measurements are too expensive and time consuming. Hence, whether displacement ventilation could help with saving energy is still debated.In general, displacement ventilation is attractive to the core region in a building since no heating is needed. However, the perimeter zones require high cooling energy.
Different guidelines have been published to provide guidance on designing displacement ventilation systems, including:
- Skistad H., Mundt E., Nielsen P.V., Hagstrom K., Railo J. (2002). Displacement ventilation in Non-Industrial Premises. Federation of European Heating and Air-conditioning Associations.
- Skistad, H. (1994). Displacement ventilation. Research Studies Press, John Wiley & Sons, Ltd., west Sussex. UK.
- Chen, Q. and Glicksman, L. (2003). Performance Evaluation and Development of Design Guidelines for Displacement ventilation. Atlanta: ASHRAE.
Step 1) Judge the applicability of displacement ventilation
Step 2) Calculate summer design cooling load.
Step 3) Determine the required flow rate of the supply air for summer cooling.
Step 4) Find the required flow rate of fresh air for acceptable indoor air quality.
Step 5) Determine the supply air flow rate.
Step 6) Calculate the supply airflow rate.
Step 7) Determine the ratio of the fresh air to the supply air.
Step 8) Select supply air diffuser size and number.
Step 9) Check the winter heating situation.
Step 10) Estimate the first costs and annual energy consumption.
List of buildings using Displacement Ventilation (DV)
|Jewish Museum Berlin||1999||Germany||Berlin||Daniel Libeskind||Exhibit space|
|Bangkok International Airport||2006||Thailand||Bangkok||Helmut Jahn of Murphy / Jahn Architects||Airport terminal|
|Hearst Tower||2006||NY||New York City||Norman Foster of Foster + Partners||Large public space|
|Newseum||2011||US||Washington, D.C.||Polshek Partnership||Large public space|
|Modesto Medical Center||2008||CA||Modesto||KP Architects||Health-care|
|St. John's University, St. John's Hall||1950s||NY||New York City||unknown||Teaching environment|
|Carnegie Hall||1891||NY||New York City||William Burnet Tuthill||Theater|
|Samuel J. Friedman Theater||1920s||NY||New York City||Herbert J. Krapp||Theater|
|National Center for the Performing Arts||2007||China||Beijing||Paul Andreu||Theater|
|The Copenhagen Opera||2004||Denmark||Copenhagen||Henning Larsen||Theater|
- Chen, Q.; Glicksman, L. (1999). Performance Evaluation and Development of Design Guidelines for Displacement Ventilation. MA.: ASHRAE.
- REHVA. (2002). Displacement Ventilation in Non-Industrial Premises. Federation of European Heating and Air-conditioning Associations.
- Novoselac, Atila; J., Srebric (June 2002). "A critical review on the performance and design of combined cooled ceiling and displacement ventilation systems". Energy and Buildings. 34 (5): Energy and Buildings. doi:10.1016/S0378-7788(01)00134-7.
- Schiavon, Stefano; Bauman, F.; Tully, B.; Rimmer, J. (2012). "Room air stratification in combined chilled ceiling and displacement ventilation systems" (PDF). HVAC&R Research. 18 (1): 147–159. Retrieved 9 December 2012.
- Svensson, A.G.L. (1989). "ordic Experiences of Displacement Ventilation Systems". ASHRAE Transactions. 95 (2).
- "NASA's Out of this World Green Building - Web Exclusives - EDC Magazine". edcmag.com. Archived from the original on 22 January 2013. Retrieved 9 December 2010.
- ANSI/ASHRAE Standard 55 (2002). Thermal Environmental Conditions for Human Occupancy
- Melikov, Arsen; Pitchurov, G.; Naydenov, K.; Langkilde, G. (June 2005). "Field study of occupants'thermal comfort in rooms with displacement ventilation". Indoor Air. 15 (3): 205–214. doi:10.1111/j.1600-0668.2005.00337.x. PMID 15865620.
- Loveday, D.L.; Parsons, K.C.; Taki, A.H.; Hodder, S.G. (July 2002). "Displacement ventilation environments with chilled ceilings: thermal comfort design within the context of the BS EN ISO7730 versus adaptive debate". Energy and Buildings. 34 (6): 573–579. doi:10.1016/S0378-7788(02)00007-5.
- Woods, Andrew W.; Mingotti, Nicola (June 2015). "On the transport of heavy particles through an upward displacement-ventilated space". Journal of Fluid Mechanics. 772: 478–507. doi:10.1017/jfm.2015.204. ISSN 0022-1120.
- Woods, Andrew W.; Mingotti, Nicola (July 2015). "On the transport of heavy particles through a downward displacement-ventilated space". Journal of Fluid Mechanics. 774: 192–223. doi:10.1017/jfm.2015.244. ISSN 0022-1120.
- Chen, Q; Glicksman, L.R (January 1, 2003). System performance evaluation and design guidelines for displacement ventilation. Atlanta: American Society of Heating, Refrigerating, and Air-conditioning Engineers, Inc. ISBN 978-1931862424.